ANSI/TIA/EIAA Approved: May 16, TIA/EIAA. Administration Standard for. Commercial Telecommunications. Infrastructure. TIA/ EIAA. This guide is intended to be used as a reference to the application of the. ANSI/ TIA/EIA A Standard. It in no way reflects all the necessary infor-. ANSI/TIA/EIA Administration Standard for the. Telecommunications Infrastructure of. Commercial Buildings. Distributed by NDS INFORMATION- TELECOM.
|Published (Last):||23 November 2018|
|PDF File Size:||11.50 Mb|
|ePub File Size:||10.11 Mb|
|Price:||Free* [*Free Regsitration Required]|
Labeling should be pervasive; cables and connecting hardware should be labeled, but so should conduits and firestops, grounding and bonding locations, racks, cabinets, ports, and telecommunications spaces.
Permanent records must cross-reference all identifier information. A04 — As before, the first element identifies the cabinet location, but this time for the far end of the cable. Each cable and each pathway must be labeled on each end, and each label should identify the termination points of both ends of the cable. Requirements For Labels All labels must use a permanent identifier that can be easily traced — that is, a useful numbering scheme.
All labels must match up with the permanent record.
This scheme must be logical in its organization, using alphanumeric characters for ease of reference. Labeling must be easily read, eua, and capable of surviving for the life of the component that was labeled. This particular cable would have a corresponding label on the other end the data center end, in this case which would read:.
The following is the color coding scheme recommended in B: The following is the color coding scheme recommended in B:. Labeling must be logical and consistent, across all locations, matching the project drawings.
The following is a simple example of a cable identifier. All jack, connector, and block hardware may be labeled on either the outlet or panel. gia
MACs must be ea and updated in the permanent records. This is port Any moves, adds, and changes MACs must be documented with a change order.
The labeling system, and the identifiers used, must be agreed upon by all stakeholders. While recommended, color coding is not required, and compliant coding may be accomplished using color labels or color bands.
Wire Color Coding While recommended, color coding is not required, and compliant coding may be accomplished using color labels or color bands. The 6006a scheme must identify the associated physical locations building, room, cabinet, rack, port, etc. The labeling principles that underlie B include the following: This particular cable would have a corresponding label on the other end wia data center end, in this case which would read: It identifies the termination point for both ends of the cable, with the near end shown first.
All labels must meet requirements for legibility, defacement, and adhesion, specified in UL Labels for station connections may appear on the face plate. PVBX, LANs, and individual computers Yellow — Auxiliary circuits, such as alarms and security systems Red — Key telephone systems termination Record Keeping Requirements Drawings 606z documents must be secured and backed up by the building administration.
These principles are then translated into specific requirements.